Product Specifications - JJA36175 - Square D Powerpact Circuit Breaker
Dimensions (HxWxD):11.48" x 4.48" x 5.87"
Protection Type:Overload protection / Short-circuit protection
Trip Unit Technology:Thermal-magnetic
Line Rated Current:175 Amp
Mounting Mode:I-Line bracket
Breaking Capacity Code:J
Electrical Connection:I-Line connection line / Lugs load
Magnetic Hold Current:875 Amp
Continuous Current Rating:80%
AWG Gauge:AWG 4...AWG 4/0 aluminium/copper terminal
Product Description - JJA36175 - Square D Powerpact Circuit Breaker
Square D, Powerpact, type JJA, 3P, ABC phase connection, 3PH, 175A, 600V, 65kA@480V, UL listed, current limiting, i-line style plug-in, suitable for reverse fed applications, complete with non-interchangeable trip, LI - Long-Time and Instantaneous trip functions, thermal magnetic, molded case circuit breakers.
Returns are easy
You may return items within 30 days of delivery for a refund.
FREE Shipping on orders over $49.
Simply Breakers offers one to five day delivery in the United States. The variation depends on the chosen shipping speed and the warehouse location for the product(s).
Same Day Shipping
We strive to ship out your items within one business day.
In rare circumstances, Simply Breakers may reserve up to 5 business days to complete shipment. Feel free to contact us if your order is time sensitive.
All products carry a 1-year warranty from Simply Breakers. All of our breakers are authentic and factory new.
JJA36175 - Square D 175 Amp 3 Pole 600 Volt Molded Case Circuit Breaker
Bought a 125 amp Square d breaker.
The best price on the internet! Beat all local prices by 40-50 bux. But local didn't have anything in stock. Would be 2 weeks to get one in.
Simply breakers not only had one, but was shipped to my door in BC from Ontario in 3 days. WOW. That's awesome!
Hooked it up today. Seems good to go.
Thanks a lot, definitely buy from again.
Breakers work great so far.
So easy and fast exactly what it's supposed to be.
A fraction of the price vs. a local electrical supplier. Installed and it worked without issue.